Automatic Gas Extinguisher Control Panel AW-GEC2169
- The AW-GEC2169 automatic gas fire extinguisher panel has the following features:
Alarm input : two alarming zone signal input , 16 detectors could be connected to each zone
EM valve output : control the output of EM valve.
Panel output: line fault output / alarm output / fire extinguishing signal output/24VDC output
Power output: resettable 24VDC output, 200mA current limit protection
Automatic power switching: 220V AC power and standby battery power can be switched automatically.
Three levels of access control (view, operation, settings)
Fault detection with display: Real-time detect working condition of input, output, system, power, ground, fuse,and so on.
Manually disable function: Manually disable the Panel functions and zones devices.
Evacuation: Manually activate the fire alarm devices.
Silence operation: Manual silence the horns alarm and panel buzzer .
Delay time setting: You can manual set the Panel reseting time and Release delay time.
Panel Security Protection : outside cabinet with Visible glass window of opening and closing door .
tability: long-term rigorous testing before leaving the factory, the Panel is stable, safe and reliable;
|AC INPUT||220VAC 50HZ||+10%|
|DC OUTPUT at Power Board||24VDC (19V-28V) and 5VDC (4.9V-5.1V)|
|Voltage for MCU||5V for power board MCU, 3.3V for others|
|Current at 24VDC from PSE||<450mA standby current|
|Maximum current from PSE||1.4A except batteries charge|
|Batteries current||1.85A maximum, current limited|
|Auxiliary output||24VDC, 200 mA max, current limited|
|Extinguishant release delay time||Adjustable 0 to 60seconds(5 second steps)|
|Imin, Imax.a and Imax.b according to EN54-2||Imin=340mA, Imax.a=424mA, Imax.b=1.4A|
|Batteries||2*12V/ 2.3Ah sealed lead acid gel, self-regulated|
|Battery replace Resistance||1.6Ω±10% if needed|
|Battery low-voltage protection||21V|
|The maximum and minimum electrical ratings for each input and output||Detectots / zone lines: 15.2V-28V Sounder lines:19-28V
Fire protection/Fire routing lines:19-28V Fault routing lines:18-28V
|Detectors wiring allowed each zone||16 points|
|Max points (detector and MCP) per CIE||32 points|
|Zone alarm current||6mA minimum/ 27mA maximum|
|Sounder output||200mA maximum|
|Fire routing/ Fault routing||200mA maximum each terminal|
|Communication protocol||2 wires RS485 bus system|
|EOL resistor for zone, inputs(Except for main power) and outputs||6.8K 1W|
|Wires for 220V AC IN (recommended)||16AWG|
|Wires connect power board to interface board (recommended)||20AWG|
|Wire for main board wiring with interface board (recommended)||28AWG|
|Fuse on power board||3A/ 250V Glass tube fuse 5*20(mm) Fast/quick blow|
|Fuses on interface board(general outputs)||0.2A /250V Glass tube fuse 5*20(mm) Fast/quick blow [*5pcs]|
|Fuse on interface board(Main Power)||2A/ 250V Ceramic tube fuse 5*20(mm) Slowly blow|
|Fuse on interface board(EM valve)||1.5A/ 250V Glass tube fuse 5*20(mm) Fast/quick blow|
|Environmental||Class A temperature range: -5 to 40°C (23~104°F)
Humidity: 5 to 95% RH, non-condensing
|Terminal blocks rating||All terminals rated for 12 to18 AWG
(0.75 to 2.5 mm2)
|Wires between interface board (Panel)and Detector (recommended)||2-core shielded cable for 12 to18 AWG
(0.75 to 2.5 mm2)